Open access peer-reviewed chapter

# Performance-Based Design for Healthcare Facilities

Written By

Wilfrid Gbenankpon Djima, Abdullah Can Zulfikar and Cüneyt Tüzün

Submitted: July 27th, 2020 Reviewed: December 1st, 2020 Published: June 30th, 2021

DOI: 10.5772/intechopen.95320

From the Edited Volume

## Natural Hazards

Chapter metrics overview

View Full Metrics

## Abstract

Healthcare buildings are one of the most critical facilities in any country for their important roles just after an earthquake. In this context, working on the resistance of healthcare facilities against earthquake is of great importance for a probable future earthquake. However, in today’s world, in either private or governmental agencies, buildings earthquake resistant design is not within the primary criteria such as social facilities and architectural details need for the residents. While the structural system in any building are often considered the most important in the performance, it represent approximately only 20% of the total building cost. Consequently, structural engineers should look the seismic performance in an extensive context, looking at all the systems of the building than just the damage to structural items and life-safety. So to response to this issue, a next generation of seismic performance-based design methodology and tools have been outlined in the FEMAP58 documents to allow engineers to query out the seismic performance of an entire building in terms of future life loss, facility repair cost and repair time and that we summarized and applied in this chapter for a six (6) story special moment frame healthcare building.

### Keywords

• Seismic Performance Assessment
• Performance-Based Design
• Earthquake Loss Assessment
• Healthcare Facilities

## 1. Introduction

Many essential facilities such as hospital buildings are in high seismic zones throughout the world, and some of them were designed and built at a time without sufficient earthquake knowledge nor performed and are consequently susceptible to earthquakes.

The typical building design process is not performance-based. In the typical process, design professionals select, proportion, and detail building components to satisfy prescriptive criteria contained within the building code. Many of these criteria were developed with the intent to provide some level of seismic performance. However, the intended performance is often not obvious, and the actual ability of the resulting designs to provide the intended performance is seldom evaluated or understood.

Therefore, it has been noted in this period generation procedures some limitations in the: accuracy and reliability of available analytical procedures in predicting actual building response, the level of conservatism underlying the acceptance criteria, the inability to reliably and economically apply performance-based procedures to the design of new buildings and the need for alternative ways of communicating performance to stakeholders that is more meaningful and useful for decision- making purposes [1]. Other limitations in the performance based-design procedure were also the non-account of non-structural equipment’s very important economically but also regarding their behavior during an earthquake. For example, 50% of the injuries and 3% of the deaths in the 1999 Kocaeli Mw7.4 earthquake were caused by non-structural elements and 30% of the losses were found to be furniture, white goods, electronic equipment and other valuable items [2, 3]. In addition, in the 1989 Loma Prieta and 1994 Northridge earthquakes, 10 large hospitals were evacuated or had to be closed due to damage caused by non-structural elements (plumbing) [4, 5].

So, to fulfill the promise of performance-based engineering, FEMA started the development of next-generation performance-based design procedures to address the above limitations. By result, it has been finalized the FEMAP58 [1, 6, 7] guideline to count not only the structural damage but also non-structural damage in the performance assessment. Specifically, others research also focused on the study of the non-structural seismic behavior and assessment and for hospital building [8, 9].

This paper provides practical guidance principally on implementing the seismic performance assessment methodology set forth in FEMA P-58-1 and the guidelines for Seismic performance assessment of buildings, [1, 10], to assess the seismic performance of individual buildings based on their unique site with structural, non-structural, and occupancy characteristics, expressed in terms of the probability of incurring casualties, repair and replacement costs, repair time. The FEMA-P58-2 Implementation Guide [2] contains examples illustrating the performance assessment process, including selected calculation and data generation procedures, by using the selected electronic materials provided in Volume 3 – Supporting Electronic Materials and Background Documentation [7, 11].

This study does a nonlinear static analysis for an existing typical six (6) story hospital building following the Turkish Building Earthquake Code [6] and the ASCE 41 [9] provisions as well as ACI-318 for reinforced concrete and masonry structure [7, 8], aiming to provide a more realistic estimate of the seismic demands and economic-effective assessment strategy. The PACT (Performance Assessment Calculation Tool) is used in the analysis of the sample hospital building [12, 13, 14].

Many financial institutions including lenders, investment funds, and insurers use Probable Maximum Loss (PML), Scenario Expected Loss (SEL), and Scenario Upper Loss (SUL) as preferred performance measures. These performance measures are quantitative statements of probable building repair cost, typically expressed as a percentage of building replacement value [1]. Some building owners, developers, and tenants have also relied on these performance measures to quantify seismic performance. In this regard, it is believed that this study will be a sample study for evaluation of seismic performance of a typical hospital building and its probable consequences.

## 2. Building description

The building is a six-stories healthcare building with a moment frame structure that has plan dimensions of 36,57 m by 54,86 m (see Figures 1 and 2). Floor-to-floor height is 4.6 m at the lower story and 4 m at other stories (see Figure 3). The structure has reinforced concrete special moment frames around the building perimeter. The floors and roof are two-way post tensioned flat slabs (0.2 m thick) supported by the perimeter moment frame and interior reinforced concrete columns on a 9.14 m by 9.14 m grid (see Figures 4 and 5). When entering the building information into the PACT direction 1 is arbitrarily aligned with the North–South (Y) axis and direction 2 is aligned with the East–West (X) building axis.

The building is designed and detailed according to the requirements of Turkish Building Codes 2018 [6, 8, 9]. Vulnerable non-structural building features include exterior glazing, gypsum board partitions, suspended acoustical ceilings, fire sprinkler system, traction elevator, concrete roof tiles on a perimeter mansard, hot and cold-water piping, and HVAC ducting.

## 3. Building performance model

The building performance model has been constructed in PACT by the following order:

• providing project information,

• building characteristics selecting fragility specifications and performance groups,

• identifying collapse fragility and collapse modes,

• and providing residual drift fragility

For this case study, information’s input is as follow (see PACT input in Figures 6 and 7):

• Number of Stories: 6.

• Total Replacement Cost: Estimated as $2500/m2 × 12960 m2 or$32,400,000.

• Replacement Time: Estimated as 825 days.

• Core and Shell Replacement Cost: Estimated as $1000/m2 × 12960 m2 or$12,960,000.

• Maximum Workers per Square Foot: Default value of 0.001 is used.

• Total Loss Threshold (as Ratio of Total Replacement Cost): Default value of 1.0 is used.

• Floor Area: 2090 m2

• Floor Height: 4 m Variation in floor height is input via the Floor Number drop down selector, which also permits input of non-typical floor areas.

Figures 8 and 9 show the PACT panel input for Population Modeling.

## 4. Structural components

### 4.1 Structural component fragility specification

The structural components are inputs based on the basic building characteristics previously described. The selection process proceeds progressively from foundations through super structure. The following information summarizes the structural components included in the performance assessment model.

For each floor, the number of special moment frame beam-column joints vulnerable to story drift in each building direction are entered for each of the pre-selected specifications. Table 1 and Figure 10 summarize the defining performance groups in PACT with A, B, C, D, E the building axes in X (2) direction and 1, 2, 3, 4, 5, 6, 7 in Y (1) direction. Input of the post-tensioned slab/column joint information is similarly inserted at each floor; however, these fragilities are input as non-directional. There are 15 joints per floor (Table 2).

Joint LocationFragility Classification NumberInput DirectionJoint LocationFragility Classification NumberInput Direction
A-1B1041.002a1A-5B1041.003b2
A-2B1041.002a2B-1B1041.003b1
A-6B1041.002a2B-7B1041.003b1
A-7B1041.002a1C-1B1041.003b1
E-1B1041.002a1C-7B1041.003b1
E-2B1041.002a2D-1B1041.003b1
E-6B1041.002a2D-7B1041.003b1
E-7B1041.002a1E-3B1041.003b2
A-3B1041.003b2E-4B1041.003b2
A-4B1041.003b2E-5B1041.003b2

### Table 1.

Fragility group selections for the beam/column components.

Fragility Classification NumberDirectionNumber Per Floor
B1041.002a14
B1041.002a24
B1041.003b16
B1041.003b26

### Table 2.

Performance group quantities for reinforced concrete elements.

### 4.2 Structural component performance group

The performance group definition process is repeated for each floor and for each direction (including non-directional) as shown in Figures 11 and 12. Table 3 summarize the total number of performance group per floor.

Storywx (kN)hx (m)whk x xCVXVx (kN)Fx (kN)Fx(V)(Kn/ml)Computed DisplacementCorresponding drift ratio
Roof32741.2424.6805434.50.2819116.45368.3084.100.12010.002
5th32741.2420.6674469.540.2319116.44495.4170.420.11210.003325
4th32741.2416.6543504.580.1919116.43622.5156.750.09880.004075
3rd32741.2412.6412539.620.1419116.42749.6243.070.08250.00595
2nd32741.248.6281574.660.1019116.41876.7229.400.05870.006275
1st32741.244.6150609.70.0519116.41003.8315.730.03360.00730434
<&$;>2868132.6119116.40 ### Table 3. Lumped weight distribution + lateral forces and story drift ratio. Advertisement ## 5. Non-structural components The process of identifying and selecting the type and distribution of the non-structural components can be greatly simplified using the Normative Quantity Estimation Tool, provided in Volume 3 of PACT. This tool can be used to generate a floor-by-floor listing of non-structural components with estimates of their performance group quantities with the simple input of building floor areas and occupancies as shown in Figure 13. To use the Normative Quantity Estimation Tool, the building floors and occupancies are entered into the Building Definition Table in the Normative Quantity Estimation Tab. Figure 14 illustrates input of this information for the example building. Figure 15 [1] is an example of fragilities curves of reinforced concrete Special Moment Frame at different damage state details in [1] and Figure 16isan example of fragility curves of different types of hospital non-structural equipment from [15]. The Figures 17 and 18 show the overview of the in-site fragility description for Special Moment Frame (SMF) and Electrical Equipment [1]. Advertisement ## 6. Collapse fragility and collapse mode The collapse fragility is defined as having a median value Ŝa(T)and a dispersion. For this purpose, we have used the non-linear static analysis approach in SAP2000 (Figures 19 and 20) and the SPO2IDA Tool in [1]. The building was modeled according to the Turkish Building Code 2018 for pushover static analysis in each building direction and the effective stiffness of reinforced concrete columns, beams and shear walls as defined in [6] Section 5 were applied. Figure 21 illustrates the results of the pushover analysis for both building direction 1 and direction 2, which are identical. After then, the coordinates of the pushover curves are input to the SPO2IDA Tool provided in [1] along with the building height (24.6 m or 80.71 feet), building weight (199235.85 kN or 44790.02 kips) and fundamental building period (1.96 seconds). Four control points are used to approximate the pushover curve as illustrated in Figure 22. Figure 23 present the results of the SPO2IDA evaluation. The value of Ŝa(T)is estimated as 1.16 g. The collapse fragility is thus defined as having a median value of Sa(T) of 1.16 g and a dispersion of 0.6 as entered into the PACT Collapse Fragility panel (Figure 24). The number of independent collapse modes which can occur and thus the probability of each is difficult to predict analytically. To figure out these data, the user must use judgment supported upon building type, structural system, experience, and analytical inferences. When using the simplified analysis approach, limited analytical information regarding potential collapse modes is out there. For this instance, just one mode of collapse is taken under consideration. More information’s gained from numerous response history analyses can give additional insight into potential collapse modes. Advertisement ## 7. Define earthquake Hazard Ground motion prediction equations provide estimates of spectral response acceleration parameters for specified earthquake magnitude and site-to-source distance based on regression analyses of past strong motion recordings. Most ground motion prediction equations provide geometric mean (geomean) spectral response accelerations represented by the quantity: Sgm=SxTSyTE1 where Sxand Syare orthogonal components of spectral response acceleration at period T. The xand ydirections could represent the actual recorded orientations, or they could represent a rotated axis orientation. Intensity-based assessments require a target acceleration response spectrum and suites of 11 pair of ground motions scaled for compatibility with this spectrum (see Figure 25). Figure 26 represents the selected ground motion pairs with geomean spectra that are similar in shape to the target response spectrum. To determine the building’s fundamental translational periods in two orthogonal directions, modal analysis is performed. The fundamental periods in x- and y-directions are 1.94 sec. and 1.98 sec., respectively. Then, the average fundamental period of the building is considered as: T¯=Tx+Ty2=1.96secE2 Advertisement ## 8. Analyze building response Simplified analysis is used to generate median estimates of peak transient drift, peak floor accelerations and residual drifts. Associated dispersions are generated using simplified analysis. Peak total floor velocities are not generated since none of the vulnerable building components use this demand parameter. A linear building model is constructed using the modeling criteria of [8], linear static procedure. ### 8.1 Estimate median story drift ratio Firstly, we determined the pseudo lateral force by the formula: V=C1C2SaT1W1E3 where C1 is an adjustment factor for inelastic displacements; C2 is an adjustment factor for cyclic degradation; Sa(T1) is the 5% damped spectral acceleration at the fundamental period of the building, in the direction under consideration, for the selected level of ground shaking; and W1 is the first modal effective weight in the direction under consideration, taken as not less than 80% of the total weight, W. Figures 27 and 28 and Table 3 show the computed lateral displacement in X (2) direction and the corresponding drift ratio. Δi=HΔiST1hiH×Δii=1toNE4 where HΔiST1hiHis the drift modification factor for story icomputed. lnHΔi=a0+a1T1+a2S+a3hi+1H+a4hi+1H2+a5hi+1H3,S1,i=1toNE5 With T1=1.96s,H=24.6m Values of a0through a5for 6 stories or less in height are provided in [1] Table 5-4 by using the strength ratio given by: S=SaTVVy1E6 The value of Vy1is taken from the pushover analysis used to estimate the collapse fragility (see SPO2IDA input, Figure 22, Elastic Segment end point) (Table 4). StoryΔihi + l/HlnHΔiHΔiΔ*i 10.00730430.18699190.20896341.23239980.0090019 20.0062750.3495935−0.0098750.9901740.0062133 30.005950.5121951−0.1070920.89844310.0053457 40.005950.6747967−0.0826880.92063790.0054778 50.0040750.83739840.06333581.06538450.0043414 60.00332510.33098071.39233290.0046295 ### Table 4. Median story drift ratio estimates. ### 8.2 Estimate peak floor acceleration At the base of the building, peak floor acceleration is taken as equal to the peak ground acceleration. At other floor levels, i, the estimated median peak floor acceleration, a*(Table 5) relative to a fixed point in space, is derived from the peak ground acceleration using: StoryPGAhi + 1/HlnHaiHaia*i 10.6950.695 20.6950.1869919−0.3579470.699110.4858814 30.6950.3495935−0.3642890.69469060.48281 40.6950.5121951−0.370630.69029920.4797579 50.6950.6747967−0.3769720.68593550.4767252 60.6950.8373984−0.3833130.68159950.4737116 roof0.6951−0.3896550.67729080.4707171 ### Table 5. Median floor acceleration estimates. ai=HaiST1hiH×PGAi=2toN+1E7 lnHai=a0+a1T1+a2S+a3hi+1H+a4hi+1H2+a5hi+1H3,S1,i=1toNE8 The coefficients of a0 through a5 for 6 stories or less in height are provided in [1] Table 5-4. ### 8.3 Estimate of dispersion for median story ratio, median peak floor acceleration, and median peak floor velocity For intensity-based, separate values of total dispersion for drift ratio, βSD, floor acceleration, βFA, and floor velocity, βFV, are needed. βSD=β2+βm2E9 βFA=βaa2+βm2E10 βFV=β2+βm2E11 These are calculated based on [1] Table 5-6 values for analysis record- to-record dispersion for drift, β, acceleration, βaa, and velocity, βav, respectively, by interpolation approach. Advertisement ## 9. Estimate median residual story drift ratio and dispersion Since the requirements for direct simulation of residual drift are computationally complex and not practical for general implementation in design, the following equations were developed to estimate the median residual drift ratio, response of the structure: Δr=0forΔΔy {Δr=0.3ΔΔyforΔy<Δ<4Δy)}E12 Δr=Δ3ΔyforΔ4Δy) where Δis the median story drift ratio calculated by analysis, and Δyis the median story drift ratio calculated at yield. The peak transient drift ratios were estimated. The yield drift ratio is obtained from the capacity curve derived from the pushover analysis used to generate the story shear at yield (Figure 29). At yield, the peak transient acceleration is determined by the equation for the building fundamental period between the range of 0.7 sec to 2 sec: SaT=Sa1T=0.755gE13 From the capacity curve, the corresponding roof displacement for the peak transient acceleration at yield then is 0.0045 m. Thus, the yield drift ratio is: Δy=0.004524.6=0.0002E14 The maximum transient drift ratio for the building occurs at the first story (Δ= 0.0090). Δr=0.009030.0002=0.0084 The median estimate of residual drift obtained from the simplified analysis method is assigned a dispersion of 0.8. Advertisement ## 10. Input response and calculate performance The median demand estimates for peak transient drift ratio, peak floor acceleration, and residual drift ratio are input to PACT for direction 1 and direction 2 in the Structural Analysis Results tab (see Figures 30 and 31). Then, PACT uses this information to make damage state assessments for all building components contained in the building model. A Monte Carlo procedure is used to assess a range of possible outcomes as repair cost and repair time. ## 11. Review results and comments As showed in the Figure 32, the estimated median repair cost is shown as$2.710.445, which corresponds to 8.37% of the building’s total replacement cost. From the isograph on the Figure 32, it is seen that the yellow stick representing the performance group B2022.001 (Curtain Walls - Generic Midrise Stick-Built Curtain wall, Config: Monolithic, Lamination: Unknown, Glass Type: Unknown, Details: Aspect ratio = 6:5), explain its contribution to the most of the building total repair cost with approximately $1.700.000. Figures 33,34, and 35 explain that 50% probability that repair cost will not exceed$2.710.445, 145 injuries, 105 deaths.

The performance results of the PACT can be examined in numerous ways. Viewing results by realization reveals that collapse plays a more significant role than residual drift (see Figure 36). For approximately 56 of the 200 realizations of the collapse of the component B1049.031 Post-tensioned concrete flat slabs-columns with shear reinforcing and, 40 of the 200 realization for the performance group B3011.011 Concrete tile roof tile secured and compliant for damage being judged irreparable.

## 12. Conclusion

Performance assessment can provide useful information for many decisions associated with real property. These include: demonstrating equivalence of alternative design approaches, selecting appropriate design criteria for new buildings, determining if an existing building constitutes an acceptable risk for a particular planned use, whether or not it should be upgraded, and if so, to what level, performing benefit–cost studies to determine a reasonable investment for improved seismic resistance in a building, determining whether or not insurance is a cost- effective risk management technique.

In this study, a case study of a typical hospital building has been analyzed. The non-linear static pushover analysis results have showed that the collapse occurs at the building base in Mode-8. The linear static analysis results have demonstrated a maximum roof displacement of 7.69 cm. Consequently, the performance assessment that used the data from these analyses have shown a low repair cost of 8.37% (less than 40%). Thus, based on the past knowledge and recommendations that suggests 40% of the total building replacement cost can be a reasonable threshold for total loss of several buildings, the decision of retrofitting can be given for this case study since the repair cost is less than 40%.

The adaptation of the current study to the typical health-care facilities in many countries as Turkey is still on-going. It is believed that the results of this study will be valuable for the building owners, managers, insurance firms and for the process of benefit–cost performance and risk management.

## References

1. 1. R. O. Hamburger Simpson Gumpertz, Heger I., C. Rojahn, J. A. Heintz, M. G. Mahoney, APPLIED TECHNOLOGY COUNCIL 201 Redwood Shores Parkway, Suite 240 Redwood City, California 94065www.ATCouncil.org, Seismic Performance Assessment of Buildings Volume 1 – Methodology, December 2018
2. 2. Petal, M. Epidemiology of Deaths and Injuries In The August 17, 1999, 3:02 A.M. M=7.4, Kocaeli Earthquake Report, BU KOERI, 2013,http://www.probina.com.tr/5UDMK/PDF/AE045_FP.pdf
3. 3. AHEB, Hastaneler İçin Afete (Depreme) Hazırlıklı Olma Kılavuzu B.Ü Kandilli Rasathanesi ve Deprem Araştırma Enstitüsü Afete Hazırlık Eğitim Projesi kapsamında yayınlanan kitap, 2004www.koeri.boun.edu.tr
4. 4. Diana T., Nicholas C., Riley M. Chung, H. S. Lew, 1994 Northridge Earthquake Performance of Structures, Lifelines, and Fire Protection Systems, May 1994
5. 5. İPEK, C., KISTIR, M.R., KUZUCUOĞLU, A.H., “Yapısal olmayan sistemlerin deprem etkileri açısından değerlendirilmesi”, International Burdur Earthquake & Environment Symposium, 2015
6. 6. R. O. Hamburger Simpson Gumpertz, Heger I., C. Rojahn, J. A. Heintz, M. G. Mahoney, APPLIED TECHNOLOGY COUNCIL 201 Redwood Shores Parkway, Suite 240 Redwood City, California 94065www.ATCouncil.org, Seismic Performance Assessment of Buildings Volume 2 – Implementation Guide, December 2018
7. 7. R. O. Hamburger Simpson Gumpertz, Heger I., C. Rojahn, J. A. Heintz, M. G. Mahoney, APPLIED TECHNOLOGY COUNCIL 201 Redwood Shores Parkway, Suite 240 Redwood City, California 94065www.ATCouncil.org, Seismic Performance Assessment of Buildings Volume 3: Supporting Electronic Materials and Background Documentation, December 2018
8. 8. Eric L., Susan P., Rob F., Ivy P., Wanda R., Design Guide for Improving Hospital Safety in Earthquakes, Floods, and High Winds, Chapter 1 and 2, June 2007
9. 9. Steven L, Matthew H.,, APPLIED TECHNOLOGY COUNCIL 201 Redwood Shores Parkway, Suite 240 Redwood City, California 94065www.ATCouncil.org, Recommendations for Improved Seismic Performance of Nonstructural Components, September 2018
10. 10. Michael M., Robert D. H., Applied Technology Council. “Guidelines for Seismic Performance Assessment of Buildings, May 2007, Available from:https://www.atcouncil.org/pdfs/ATC-58-50
11. 11. Djima W., A Thesis Submitted for the Degree of Master of Science/Department of Civil Engineering/Earthquake and Structural Engineering Program, Performance Based Design and Its implementation Tool in Healthcare Facilities, Chapter 3 and 4, June 2020
12. 12. ASCE/SEI 7, American Society of Civil Engineers, Reston Virgini, Minimum Design Loads for Buildings and Other Structures, pp. 7–9–13-109-117-119-142-153-160-177-185-243, December 2005
13. 13. ACI, Building Code Requirements for Masonry Structures and Specifications for Masonry Structures, 530/530.1–2008 May
14. 14. ACI 318, Building Code Requirements for Structural Concrete and Commentary, pp 83–107–239-323-329, August 2011
15. 15. Turkey Building Earthquake Code (TBEC-2018), Sections, 5 and 15, 2018

Written By

Wilfrid Gbenankpon Djima, Abdullah Can Zulfikar and Cüneyt Tüzün

Submitted: July 27th, 2020 Reviewed: December 1st, 2020 Published: June 30th, 2021