Explanation of geometric shapes from Figure 1.
This chapter deals with the influence of the electric field on a Medium Voltage Indoor Post Insulator (MVIPI) with standard and modified external shapes. The goal of this chapter is to show the electric field behavior of the MVIPI with different external shapes and to introduce a numerical model with a favorable distribution of the electric field that relieves the dielectric from stress. The chapter describes an MVIPI with nominal voltage 20 kV AC and shows an existing MVIPI, an MVIPI with a different number of ribs, and an MVIPI with exceptional external shape. The MVIPI’s new external shape does not have the typical shape of the ribs, but a new outline, using the Lagrange polynomial, that will acquire its optimal form through the optimization process. A Differential Evolution optimization algorithm is used for the optimal design of the insulator’s external shape. The value of the Electric Field Strength (EFS) will be minimized within the permissible bounds during the optimization process. The important parameters during the minimization of the objective function are the value of the EFS in the interior and exterior of the insulator. EFS values are shown for every MVIPI example and are compared with the existing MVIPI. The obtained results are analyzed and discussed.
- electric field
- medium voltage
- indoor post insulator
Medium voltage indoor post insulators (MVIPIs) are the most common elements used in switchgear . They are the significant components of electric power devices . Electric insulation of conductive parts from the grounded parts is the primary task of the insulator . Porcelain was used firstly as an insulator’s material. Various epoxy resins appeared in the mid-60s, combined with various binders, glues, and fillers. Composite insulators are being produced increasingly recently for indoor and outdoor mounting. Araldite MVIPI (Figure 1a) is most used for internal mounting and has great insulation, mechanical, and thermic properties. With small dimensions, the MVIPI has a compound form and long lifespan .
The insulator model was built in MATLAB software, which has a dual task. Firstly, MATLAB does the task of a preprocessor, which is described in Section 2. MATLAB’s second task is application of the optimization process. The selected optimization algorithm Differential Evolution (DE) [5, 6] is written and executed in MATLAB, which is described in Section 5, where the minimization of the objective function has been implemented. The essential parameter of the objective function is the value of EFS in the interior and exterior of the insulator. During the optimization process, the value of the EFS will be reduced within the admissible bounds and will be calculated using EleFAnT software .
The chapter is organized as follows. An existing MVIPI model is described in Section 2. Section 3 describes the MVIPI with a different number of ribs. Section 4 describes the novel-designed MVIPI using the Lagrange polynomial. The optimization calculation of the MVIPI’s external shape and the best position of internal insulator components using DE algorithm is described in Section 5, with the Conclusion given in Section 6.
2. MVIPI model
The existing MVIPI has six ribs (Figure 1). The MVIPI’s parts are labeled with the numbers stated in Table 1, which also shows the materials and the potentials of each component required for the calculation of the electric field.
The complete MVIPI model geometry is generated using a mesh generator, which is part of the preprocessor. The mesh generator distributes the whole problem area into finite elements [8, 9, 10], which are isoparametric quadrangular elements in the case of axisymmetric model. The problem is separated into single geometric shapes that belong to respective types of material. There are seven geometric shapes: surrounding area (1), upper right connector (2), upper indicator electrode (3), capacitor (4), resistor (5), bottom electrode (6), and insulation material (7).
The upper right connector and upper indicator electrode are connected to high voltage. Their function is to connect the conductor (i.e., contact, busbar) on the insulator. The bottom electrode is grounded and functions to attach the insulator on grounded infrastructure (i.e., cells’ housing).
The ceramic capacitor helps in achieving appropriate capacitance, defined by Standards IEC 61958  and IEC 61243–5 . The capacitance must be between 74 and 88 pF, according to [11, 12]. The electric field in the air and the outside surface of the MVIPI has to be less than 3 MV/m and inside the insulator less than 30 MV/m.
The MVIPI’s designing requires input data, such as insulator geometry, materials, and boundary conditions. Potential’s value passes from the source potential (upper indicator electrode) to the grounded part (bottom electrode). The Dirichlet boundary condition 0 V is on the right edge of the MVIPI’s model. The material is described by means of the dielectric permittivity, which, for araldite, is
Figure 2 shows a plot of the existing MVIPI’s EFSs. Figure 3 shows EFSs at different distances from the core of the MVIPI. As is apparent in Figure 3, the values of EFS are within the defined bounds (at 2, 10, and 20 mm), the dielectric strength is not exceeded (30 MV/m). Also, there was no excess of the EFS (3 MV/m) in the air (at 30, 40, and 50 mm).
3. MVIPI with a lower and higher number of ribs
Modeling of the MVIPI’s exterior is presented in the following. Examples of an MVIPI with lower and higher number of ribs are shown and compared with the existing MVIPI. Figure 4a shows the EFS of the MVIPI with five ribs. Figure 4b shows the EFS of the MVIPI with nine ribs. Figure 5 shows the comparison of the EFS between the existing MVIPI and MVIPIS with five and nine ribs at different distances from the core of the MVIPI.
The EFS of the MVIPI with five ribs is marked with a dotted line (Figure 5); a solid line marks the EFS with nine ribs, and a dashed line represents the EFS of the existing MVIPI. There is no significant change in the electric field in the interior of the insulator (Figure 5a–5c). The EFS values in Figure 5d and 5e are approximately equal; the electric field is distributed better at the insulator with nine ribs. The differences between EFS values are negligibly small in Figure 5f.
4. MVIPI with the exceptional external shape
The following presents the developing MVIPI’s new external shape (Figure 7). The designed insulator exterior, as such, does not have the characteristically shaped ribs, since it has been acquired by using the Lagrange interpolating polynomial of sixth degree (Figure 6a) . Lagrange’s interpolating polynomial for a set of
Taking into account the short form for the product of the differences (2) in (1) over (3), the final form is acquired for the Lagrange interpolation polynomial (4) 
For the sixth-degree polynomial, seven points are needed , which are labeled with
followed by the calculation of
After calculation (6), the next values are obtained:
therefore, the obtained values are
Intermediate polynomials are used before the final polynomial form . For
The sixth-degree polynomial  that will go through the points
The sixth-degree polynomial that replaces the shape of the MVIPI’s ribs is shown in Figure 6b.
The MVIPI’s novel external shape is shown in Figure 7, with the EFS value. Figure 8 compares EFS values between the existing MVIPI (dashed line) and the MVIPI with the novel external shape (solid line). The values of EFS are within the defined bounds, with the exception of the boundary insulator to air (30 mm from the insulator core), where the EFS value of the MVIPI with the new external shape exceeded the permissible value slightly 3 MV/m (3.28 MV/m). The lowest possible value of EFS is wanted in that area; hence, the coefficients of the polynomial will be optimized with the goal of reducing the EFS at the boundary insulator to air and finding the best position of the internal components of the MVIPI.
5. Best external shape and the position of the internal MVIPI’s components’ calculation by means of the differential evolution algorithm
DE is a fast and robust population-based direct-search stochastic optimization algorithm that was first introduced by Storn and Price . This algorithm is widespread among engineering audiences [2, 3, 13, 14, 15, 16, 17] due to its robustness in reaching global minima, suitable for solving nonlinear and constrained optimization problems. It requires only boundaries of expected solutions and has only a few control parameters to be defined. A detailed description of the DE algorithm is available from [5, 6].
The component to be optimized is written mathematically in the form of an objective function. In this chapter, the criterion of optimizing is the value of EFS in the most stressed points, which are settled in the air just above the insulator-to-air intersection , from the top of the insulator through ribs to the bottom of the insulator. The electric field, is in these points, defined as
The wanted value
Due to the optimization process of minimization of the EFS, the parts of the geometric areas of the MVIPI are written parametrically (polynomial coefficients, upper right connector, the distance between the resistor and the bottom electrode). By adjusting the parameters, the shape of the MVIPI will occur in which the value of the electric field is the lowest at critical points. Boundaries are determined by the parameters, within which they will be alternated [2, 3].
In total, there are six parameters that are labeled from
|Parameter||Minimum value||Maximum value||Value before optimization||Value after optimization|
Figure 10 shows the MVIPI’s EFS distribution after the optimization. Figure 11 shows EFS at different distances from the center of the MVIPI. The solid line marks the EFS of the novel-designed MVIPI after the optimization. The EFS of the novel-designed MVIPI before the optimization is marked with a dotted line. The EFS of the existing MVIPI is marked with a dashed line.
Comparing the results before the optimization, there was a decrease in the EFS inside the insulator and in the air after the optimization. 30 mm from the MVIPI’s core (Figure 11d), the EFS does not exceed the value of 2 MV/m on the boundary insulator to air. Comparing EFS value between the novel-designed MVIPI before and after the optimization, there is a 35% decrease in the EFS at the same distance after the optimization. On the other hand, comparing EFS values between the existing MVIPI and novel-designed MVIPI after the optimization, there is a 22% decrease in the EFS at the same distance after the optimization.
This chapter describes the influence of the electric field on the MVIPI with standard and modified external shapes. The electric field behavior of the MVIPI with different external shapes was shown, and the numerical model was introduced with a favorable distribution of the electric field. The MVIPI’s external shape influence on the electric field is researched by means of changing the number of ribs and making a completely new external shape of the MVIPI, which does not have the typical shape of the ribs, but a new outline, using the Lagrange polynomial that has acquired its best form through the optimization process.
The application of the DE algorithm is shown in order to design the MVIPI’s external shape and reach the best position of internal insulator elements. It was essential to satisfy the criteria for reaching a certain boundary of EFS inside and in the surrounding area of the MVIPI.
The improved novel-designed insulator, with its modified external shape, is returned mainly in the lower value of the electric field inside the insulator and in the air, which means less exertion of insulation material. Such an MVIPI can function over a long period of time. Producing such an MVIPI is also less challenging, due to the fewer elements inside the insulator and, thus, fewer risks for partial discharges. Another major achievement is scrap decrease, which is economically noteworthy. The tool for molding the MVIPI’s external shape is less complex, which is favorable for production and that it will be less possible to form cavities in the casting.
|E||electric field strength [V/m]|
|EW||wanted value of the electric field strength [V/m]|
|Mn(r); m(r)||Lagrange interpolating polynomial|
|n||number of data points|
|NP||size of the population|
|p1,…, p6||parameters of the insulator|
|(r, z)||coordinates [m]|