Desorption amount and temperature rise
In recent years, humidity control has been recognized as one of the important technologies in various fields; e.g., the system is required to maintain comfortable indoor air quality in household sector, and to improve the quality of products in industrial sector. In general, controlling the humidity through temperature, as in the case of conventional systems, appears to be an energy consuming process, and, depending to the operation conditions, does not assure the demand levels for humidity and temperature. Under these circumstances, desiccant humidity conditioner, which makes use of adsorption/desorption phenomena of porous adsorbent, has been gaining a great attention as an environmental friendly humidification/dehumidification system because of its advantages in the following points:
It consumes very little electrical energy, and for regeneration process it allows the use of solar energy and waste energy.
It is efficient when latent heat load is larger than the sensible load.
It is a clean technology, which can be used to condition the internal environment of buildings and operates without the use of harmful refrigerants.
The achieved control of humidity is better than that when using vapor compression systems.
In some cases the cost of energy to regenerate the desiccant is less than that when compared with the cost of energy to dehumidify the air by cooling it below its dew point.
Improvement in indoor air quality is more likely due to the normally high ventilation.
It has the capability of removing airborne pollutants.
The technology of adsorptive desiccant cooling presents interesting prospects as regards market penetration (Ando & Kodama, 2005; Davanagere et al., 1999; Elsayed et al., 2006, 2008; Ge et al., 2008; Halliday et al., 2002; Hamed, 2003; Kabeel, 2007; Kodama et al., 2005; Mavroudaki et al., 2002; Oshima et al., 2006).
The desiccants are natural or synthetic substances capable of absorbing or adsorbing water-vapor due to the difference of water-vapor pressure between the surrounding air and the desiccant surface. Typical adsorptive desiccant cooling process mainly consisting of a rotary dehumidifier (D-hum) and heat exchanger can be driven with low-temperature heat energy like solar energy or waste heat, and it has been expected to be alternative air conditioning considering various energy/environmental problems such as global warming. In the solid desiccant system, a desiccant, which is coated with silica gel or zeolite, is generally used as an adsorber/desorber. During the desorption process of the system, hot air is generally used as a heating medium, and the heating of air is carried out using a solar collector, electric heater, and exhaust heat in some industrial factories. However, indirect heating with hot air, especially with the one generated by an electric heater, results in consumption of large amount of energy for regeneration, because of the fact that, the heating of air is required to heat entire desiccant rotor consisting of an adsorbent and rotor matrix. As a result, the system is characterized by low heating efficiency. In addition, excess temperature rise in the rotor during desorption process causes low water adsorptivity of an adsorbent in the following adsorption process. Moreover, when regeneration is performed with lower thermal energy below 80°C, humidification/dehumidification performance greatly decreases due to insufficient water desorption. This problem has been discussed and the optimization of adsorption-desorption process has been examined in the field of the desiccant air-conditioning, but it has not got an essential solution yet (Hamamoto et al., 2004; Harshe et al, 2005; Kodama et al., 2005).
The method for application of the microwave irradiation as a regeneration heat source of the adsorption material is considered as a strategy to the above mentioned problems.Microwave irradiation has a great advantage of direct and rapid heating of material due to self-heating of a material under microwave irradiation, which consequently results in heating of only adsorbent containing adsorbed water without heating the surrounding air (as shown in Figure 1) (Bradshaw et al., 1997, 1998; Cherbanski & Molga, 2009; Kuo, 2008; Polaert et al., 2007, 2010; Yan et al., 2004, 2007).
Hence, in the process of water desorption, there is a possibility that adsorbed water is selectively heated by microwave irradiation rather than the adsorbent, resulting in an enhancement of desorption with lower energy consumption. Based on the above mentioned advantages of microwave heating, we have proposed the novel hybrid regeneration process, which combines microwave heating and conventional hot air heating. By combining both heating methods, the hybrid system shown in Figure 2 is expected to achieve highly energy efficiency for regeneration due to direct and rapid heating by microwave irradiation as well as low thermal energy utilization provided by hot air heating. The system also has a feature of promotion of lower heat utilization by assisting water desorption with an additional energy of microwave.
Some researches have been carried out on the application of microwave heating to the regeneration of adsorbent for desiccant air conditioning. Ohgushi and Nagae have investigated heating and dehydration characteristics of various zeolites with microwave heating for the reusable desiccant in home, and reported that the mixture of Na-X and Ca-X was useful to prevent the thermal runaway (Ohgushi & Nagae, 2003). Concerning the durability of zeolite mixtures against microwave heating, they have also indicated 1.3% degradation of water adsorptivity after each MW irradiation (Ohgushi & Nagae, 2005).
In previous study, we paid attention to zeolite that showed strong water-vapor desorption capability as an adsorbent, and microwave irradiation effect was examined in water-vapor desorption of zeolite 13X (Saitake et al., 2007). As a result, the maximum desorption rate was found to be about 5 times higher for microwave heating at 800 W than that obtained for hot air heating. It was also observed that the amount of water desorbed from zeolite particles by microwave heating was 1.6-2.0 times larger than that by hot air heating, regardless of microwave power.
However, almost all experiments have been performed with powder or granular adsorbent, and there are very few researches on water desorption from desiccant rotor with microwave heating. Microwave desorption feature of these zeolite is almost unknown. Therefore, it is essential to grasp the influence of condition such as flow rate and temperature of air on desorption rate to establish the HM with microwave heating condition.
In this research, the examination of two items as follow was performed under the above-mentioned viewpoints that are;
Experimental study was performed about the influence of adsorption equilibrium and pore architecture in desorption of microwave heating by three zeolites.
Experimental study was performed about the influence of gas flow rate and temperature in desorption of microwave heating.
3 kinds of zeolite samples (4A, OXYSIV-5 and DF-9, average particle size fraction of 500μm) (made by UNION SHOWA K.K., Japan) were used. The pore size of samples is 0.4nm, 0.8nm and 1.0nm. The water-vapor adsorption and desorption isotherms were measured by water-vapor adsorption device (Belsorp aqua3, BEL JAPAN, INC.) at 30°C and shown in Figure 3.
The adsorption amount of water-vapor on 4A and OXYSIV-5 rise sharply in the range of the relative humidity, RH, below 5%, and then increased gradually. For 4A, the adsorption amount of water-vapor below 5% of RH accounts for 75% of the total adsorption amount. In addition, the adsorption amount of 4A is smaller than that of OXYSIV-5. For DF-9, the adsorption amount of water-vapor rise sharply in the range of the relative humidity, RH, below 10%, and then increased gradually almost similar to that of OXYIVE-5. The adsorption amount of water-vapor below 10% of RH accounts for 84% of the total adsorption amount which is 1.3 times larger than that of OXYSIV-5. In addition, the water-vapor adsorption and desorption of 4A and DF-9 showed desorption hysteresis, which is smaller than that of OXYSIV-5.
on, visual check and measurement of water-vapor adsorption and desorption isotherms was carried out after the microwave irradiation experiment. As a result, the damage and the transformation of the zeolites by microwave irradiation were not observed. Moreover, change of adsorption and desorption isotherms by the existence or nonexistence of microwave irradiation was not observed as shown as Figure. 3.
2.2. Experimental apparatus and method
The experimental apparatus, as shown in Figure 4, consisted of a microwave irradiator, a circulated packed adsorption, an evaporator, a microwave absorber, a heater and thermometers. To keep the apparatus on a constant temperature (30°C), the insulant was used to enclose the apparatus.
Microwave was oscillated at 2450MHz, passed a cylindrical waveguide of 110mm in the diameter (TE11 mode) through a rectangular waveguide (TE01 mode), and was absorbed by the microwave absorber. The circulated type absorption column was vertically set at 140mm from the entrance and in the center of section of the circular waveguide. The position where the adsorption column was set up was the position where the electric field strength of microwave was the maximum. The humidity-temperature meters (PosiTector DPM, DeFelsko Corp.) were set up in each gateway of the circulation air was calculated from the measurement of temperature and humidity difference, and the amount of adsorption and desorption were calculated based on those. The fiber-optic thermometer was inserted in the center part of the adsorbent packed bed to measure the temperature, and this temperature was assumed to be a representative temperature of the adsorbent packed bed.
The samples bed (particle diameter: 0.3-1.0mm, adsorbent bed thickness: about 2.5mm (0.5g)) in adsorption column was set in the position where electric field intensity of microwave waveguide was the maximum. In this study, a micro heater (20W) is inserted in the sample bed upper which is a circulated packed adsorption column. The adsorbent bed temperature was adjusted with heating the circulation gas by electric power (shown in Figure 5). In microwave heating experiment, microwave irradiation was carried out with the supply of this measurement electric power.
The following two desorption experiments were carried out.
After zeolites were packed into the adsorption column, the adsorption column was heated and kept at 350°C. The N2 gas of 99.99% was circulated enough to dry the adsorption column as a pretreatment. Adsorption process was carried out by circulating N2 gas of relative humidity 40% to adsorption column at 3.18m/min. Desorption process was carried out by microwave heating under conditions of N2 gas of 30°C with relative humidity 40%, gas flow rate of 1.62-6.36m/min and microwave power of 800W as comparison.
After the adsorption of DF-9 became equilibrium like 1) (flow rate: 3.18m/min), the desorption experiments was carried out by supplying power (electric power can heat 40 to 80°C of adsorbed bed achieving temperature.) and microwave heating (microwave output; 50W).
In experiments, temperature in the center of adsorbent bed and humidity of exit of adsorbent bed were measured, and the desorbed amount was calculated by using this result.
3. Results and discussions
3.1. Comparison of microwave heating desorption effect in different zeolites
As shown in Figure 6, for 4A and DF-9, heat and mass transfer behavior of microwave heating desorption process under the condition that adsorption column inlet temperature is 30°C and relative humidity is
However, for the different type of the zeolites, temperature (
q’ and T’ are defined as follows. In this experiment, adsorbent temperature rises with microwave irradiation. On contrast, adsorbent bed inlet temperature are constant at 30°C and RH=40% (absolute humidity: H=0.0106kg/kg-air). Therefore, relative humidity in the bed decreases because adsorption bed temperature rises, q’ is equilibrium adsorption amount difference corresponding to this temperature rise on isotherms. In this calculation, Clausius-Clapeyron Equation (Arogba, 2001; Kolaczkiewicz & Bauer, 1985; Kondaurov, 2003) was used based on adsorption isotherm of two temperatures of various zeolites.
The following was observed from Table 1, Figure 7 and Figure 8.
Amount order of qMW is DF-9 > OXYSIV-5 > 4A. qMW of 4A and OXYSIV-5 are 0.36 times and 0.73 times of DF-9, respectively.
Amount order of qMW/qE is also DF-9 > OXYSIV-5 > 4A. This value was slightly smaller than DF-9 in OXYSIV-5. In contrast, qMW/qE of 4A was 0.54 times of DF-9.
Amount order of TMAX is DF-9 > 4A > OXYSIV-5.
Rq of each zeolite samples shows more than 1. Rq of 4A and DF-9 was about 1.4 times and 1.6 times of OXYSIV-5. TD of 4A and DF-9 is about 0.9 times and 3.0 times of OXYSIV-5.
Temperature rise rate (ΔT/Δθ) is a little different with the type of the zeolites in desorption early time, but there is no big difference in change. The beginning desorption is the maximum, and then this value decreases afterwards.
On the other hand, adsorption rate shown the maximum in 0.98-1.0 of (1−qMW/qE) for DF-9 and 4A, and then decreased with the decrease of (1−qMW/qE) afterwards.
The above mentioned result of 1) shown that qMW of the adsorbent became small with small equilibrium adsorption amount under this experimental conditions. But, equilibrium adsorption amount of OXYSIV-5 is 0.76 times of DF-9, and this value is approximately same as 0.73 times in qMW. However, although equilibrium adsorbed amount of 4A is 0.67 times of DF-9, qMW decreases greatly with 0.36 times.
In the range of this experiment, the water-vapor adsorption can be considered influenced by pore size with same shape of temperature rise rate of adsorbents (Figure 7). This is also shown in 6), the maximum desorption rate of 4A (pore size: 0.4nm) is 0.33 times of DF-9 (pore size: 0.8nm) and 0.38 times of OXYSIV-5 (pore size: 1.0nm). On the other hand, pore size of DF-9 is slightly small compared with that of OXYSIV-5, but desorption rate is considered depending on the adsorption amount, and the desorption rate is quick up with the large equilibrium adsorption amount.
For the result of Rq in result 4), the same desorption effect of 4A and DF-9 are shown same as that of OXYSIV-5. And the effect is different with the type of zeolites. Concretely, Rq is 1.4 times while beginning adsorbed amount of 4A when OXYIVE-5 is 0.88 times in the same experiment condition. This shows that desorption by microwave heating is more advantageous than by hot air heating in zeolite with small pore size. On the other hand, the beginning adsorption amount of DF-9 is 1.3 times and Rq is 1.6 times compared with OXYIVE-5. This shows that microwave heating is effective in desorption of zeolite which is adsorbing water-vapor in large quantity.
To confirm desorption effect of the microwave more clearly, other experiments results of OXYSIV-5 are shown in Figure 9 and Figure 10. These figures shows the adsorbent bed temperature and the desorption amount change in microwave heating desorption (microwave output: 800W) and hot air heating desorption at the adsorption column inlet temperature of 30°C and RH=40%. TMW in figure is the adsorbent bed temperature by microwave heating. In addition, THE is adsorbent bed temperature under hot air supply condition that performed hot air heating to show increased temperature as same as TMW. And, qHE is desorption amount of water by hot air heating. THE and TMW almost draw the same curve according to Figure 9. On the other hand, adsorption ratio of microwave heating (1−qMW/qE) is larger than adsorption ratio of hot air heating (1−qHE/qE) at all time. It is especially remarkable in beginning desorption. As for this, microwave heating causes desorption more than hot air heating desorption. It is shown that it is more effective under the condition with much adsorption water.
TD of 3) shows decreasing effect of heat source temperature by microwave heating. This value also changes with the type of the zeolites. This value is especially excellent in DF-9. Specifically, It corresponds to desorption amount when desorption of hot air temperature 93.7°C uses hot air temperature 50.1°C together with microwave heating, and the decrease of 43.6°C of temperature of heat source becomes possible.
3.2. Influence of flow rate and hot air temperature exerted on microwave heating desorption
Desorption ratio (qMW/qE) and adsorbent bed highest achieving temperature (TMAX) obtained from results of DF-9 under the conditions of three flow rates are shown in Table 2. It’s observed that qMW shows the minimum by flow rate and TMAX decreases with increase of flow rate. It is considered as following,
Desorption rate increases with increase of flow rate and adsorption temperature.
The increase of flow rate inhibits the temperature rise of adsorbent bed, and reduces the desorption rate.
|Flow rate [m/min]||
In order to clarify the influence of hot air temperature exerted on microwave heating desorption (preset temperature: 45°C), adsorbent temperature change and desorption amount change of DF-9 desorption experiment by hot air and microwave hybrid system are shown in Figure 11. The following are observed from this figure.
Adsorbent bed centre temperature by hot air heating is almost adjusted to preset temperature. Moreover, adsorbent bed temperature TMW of microwave irradiation heating shows higher than THE.
The maximum amount change of hot air desorption shows up in about 4 minutes, and go back to the initial value in about 17 minutes. Desorption amount change of microwave heating begins to decrease after becoming the maximum in about 2 minutes, and the value is maintained for about 2 minutes longer, and appears larger than the initial value in 17 minutes.
These tendencies were similarly observed through changing hot air temperature. Then the qMW and qHE corresponding to adsorbent bed temperature TMW and THE were calculated and shown in Figure 12 after the desorption started 10 minutes. The temperature of the equal desorption amount is TMW< THE. In addition, the difference of the temperature ΔT (=THE−TMW) is equivalent to the temperature of heat source decrease effect. TMW shows the decrease effect of 16.5°C, 13.2°C and 8.6°C that obtained respectively at 45°C, 60°C and 70°C. Heat source temperature decrease effect decreased with the increase of TMW.The reason is considered as the loss coefficient of the microwave for the water decreased with increase of temperature (Koshijima et al., 2004). Moreover, ΔT is smaller than TD. This depends on the microwave output being small.
The water-vapor desorption characteristics due to microwave heating adsorption equilibrium characteristics and pore size different types of zeolites were evaluated, and the following results were gained.
The effect of microwave irradiation was approved to be better than that of hot air heating in any zeolites. This effect is remarkable for zeolite that has small pore size (4A) or large adsorption amount of water-vapor (DF-9). The desorption amount of water-vapor from zeolites by microwave irradiation was 2.22 (4A) and 2.59 (DF-9) times larger than that by hot air heating.
The desorption rate increased along with large pore size of zeolites. Moreover, the desorption rate of similarly sized zeolites increased with the increase of the adsorption amount.
The desorbed effect of microwave irradiation according to the results of the temperature rise experiments during hot air heating was confirmed as same as the effect of microwave irradiation.
The minimum value of desorption ratio appeared with the air flow rate change.
On the same desorbed amount standard, the temperature of hot air and microwave irradiation hybrid type is lower than that of hot air heating. The microwave irradiation showed the effect of maximum 16°C decrease of the heat source.
As shown above, in this research, the speeding-up of desorption and the effect of heat source temperature decrease can be confirmed by microwave irradiation.
As challenges for the future research, it is necessity to study the uniform heating method of the adsorbent. So it's necessary to consider the shape of the adsorbent and microwave irradiation method.
When applying for microwave irradiation in the desiccant humidity conditioner, it's necessary to examine microwave irradiation method and the rotor shape etc. In addition, grasp of the microwave irradiation effect by low-humidity environment is necessary for upgrading the desiccant humidity conditioner.
||absolute humidity||[kg-H2O/kg-dry air]|
||adsorption amount of water||[kg-H2O/kg-zeolite]|
||desorption amount of water calculated from temperature rise of zeolite bed||[kg-H2O/kg-zeolite]|
||equilibrium adsorption amount of water||[kg-H2O/kg-zeolite]|
||desorption amount of water by hot air heating||[kg-H2O/kg-zeolite]|
||desorption amount of water by microwave heating||[kg-H2O/kg-zeolite]|
||temperature of zeolite bed calculated from desorption amount of water||[°C]|
||temperature of zeolite bed during hot air heating||[°C]|
||temperature of zeolite bed during microwave irradiation||[°C]|
Ando K. Kodama A. 2005 Experimental Study on a Process Design for Adsorption Desiccant Cooling Driven with a Low-Temperature Heat. , 11(July 2005), 631 636
Arogba S. S. 2001 Effect of Temperature on the Moisture Sorption Isotherm of a Biscuit Containing Processed Mango (Mangifera Indica) Kernel Flour. , 48 2(May 2001), 121 125
Bradshaw S. M. Van Wyk E. J. De Swardt J. B. 1997 Preliminary Economic Assessment of Microwave Regeneration of Activated Carbon for the Carbon in Pulp Process. , 32 3 131 144, 0832-7823
Bradshaw S. M. Van Wyk E. J. De Swardt J. B. 1998Microwave Heating Principles and the Application to the Regeneration of Granular Activated Carbon. , 98 4(July/August 1998), 201 210, 0003-8223X
Cherbanski R. Molga E. 2009 Intensification of Desorption Processes by Use of Microwaves-An Overview of Possible Applications and Industrial Perspectives. , 48 1(January 2009), 48 58
Davanagere B. S. Sherif S. A. Goswami D. Y. 1999A Feasibility Study of a Solar Desiccant Air-Conditioning System-Part I: Psychrometrics and Snalysis of the Conditioned Zone. , 23 1(January 1999), 7 21
Elsayed S. S. Miyazaki T. Hamamoto Y. Akisawa A. Kashiwagi T. 2006 Analysis of an Air Cycle Refrigerator Driving Air Conditioning System Integrated Desiccant System. , 29 2(March 2006), 219 228
Elsayed S. S. Miyazaki T. Hamamoto Y. Akisawa A. Kashiwagi T. 2008 Performance Analysis of Air Cycle Refrigerator Integrated Desiccant System for Cooling and Dehumidifying Warehouse. , 31 2(March 2008), 189 196
Ge T. S. Dai Y. J. Wang R. Z. Li Y. 2008 Experimental Investigation on a One-Rotor Two-Stage Rotary Desiccant Cooling System. , 33 12(December 2008), 1807 1815
Halliday S. P. Beggs C. B. Sleigh P. A. 2002 The Use of Solar Desiccant Cooling in the UK: a Feasibility Study. , 22 12(August 2002), 1327 1338
Hamamoto Y. Murase S. Okajima J. Matsuoka F. Akisawa A. Kashiwagi T. 2004 Analysis of Heat and Mass Transfer in a Desiccant Rotor. , 21 1(March 2004), 63 75, 1344-4905
Hamed A. M. 2003 Desorption Characteristics of Desiccant Bed for Solar Dehumidification/Humidification Air Conditioning Systems. , 28 13(October 2003), 2099 2111
Harshe Y. M. Utikar R. P. Ranade V. V. Pahwa D. 2005 Modeling of Rotary Desiccant Wheels. , 28 12(December 2005), 1473 1479
Kabeel A. E. 2007 Solar Powered Air Conditioning System Using Rotary Honeycomb Desiccant Wheel. , 32 11(September 2007), 1842 1857
Kodama A. Watanabe N. Hirose T. Goto M. Okano H. 2005 Performance of a Multipass Honeycomb Adsorber Regenerated by a Direct Hot Water Heating. , 11(July 2005), 603 608
Kolaczkiewicz J. Bauer E. 1985 Clausius-Clapeyron Equation Analysis of Two- Dimensional Vaporization. , 155 2-3, (June 1985), 700 714
Kondaurov V. I. 2003 The Clausius-Clapeyron Equations for Phase Transitions of the First Kind in a Thermoelastic Material. , 68 1 65 79
Koshijima T. Shibata C. Toishi T. Norimoto K. Yamada S. 2004, NTS Inc., 978-4-86043-070-2Tokyo, Japan
Kuo C. Y. 2008 Desorption and Re-Adsorption of Carbon Nanotubes: Comparisons of Sodium Hydroxide and Microwave Irradiation Processes. . 152 3(April 2008), 949 954
Mavroudaki P. Beggs C. B. Sleigh P. A. Halliday S. P. 2002 The Potential for Solar Powered Single-Stage Desiccant Cooling in Southern Europe. , 22 10(July 2002), 1129 1140
Ohgushi T. Nagae M. 2003 Quick Activation of Optimized Zeolites with Microwave Heating and Utilization of Zeolites for Reusable Desiccant. , 10 2(June 2003), 139 143
Ohgushi T. Nagae M. 2005 Durability of Zeolite Against Repeated Activation Treatments with Microwave Heating. , 12 4(October 2005), 265 271
Oshima K. Yamazaki M. Takewaki T. Kakiuchi H. Kodama A. 2006 Application of Novel FAM Adsorbents in a Desiccant System. , 32 6(December 2006), 518 523, 0038-6216X
Polaert I. Ledoux A. Estel L. Huyghe R. Thomas M. 2007 Microwave Assisted Regeneration of Zeolite. , 5A117
Polaert I. Ledoux A. Estel L. Huyghe R. Thomas M. 2010Adsorbents Regeneration Under Microwave Irradiation Fordehydration and Volatile Organic Compounds Gas Treatment. , 162 3(September 2010), 941 948
Yan C. T. Shih T. S. Jen J. F. 2004 Determination of Aniline in Silica Gel Sorbent by One-Step in Situ Microwave-Assisted Desorption Coupled to Headspace Solid-Phase Microextraction and GC-FID. , 64 3(October 2004), 650 654
Yan C. T. Jen J. F. Shih T. S. 2007 Application of Microwave-Assisted Desorption/Headspace Solid-Phase Microextraction as Pretreatment Step in the Gas Chromatographic Determination of 1-Naphthylamine in Silica Gel Adsorbent. , 71 5(March 2007), 1993 1997
Yoshida H. 2005, Fuji Technosystem, 978-4-93855-596-2Tokyo, Japan